Ventura, CA business & property owners in need of HVAC or refrigeration design, installation, maintenance, monitoring, repair or retrofits have called RESSAC first for the past 90 years. That’s because we are a third-generation, family owned company that prides itself in exceptional customer support, timely response and quality service. Don’t take our word for it, read our reviews below to learn more.
for Ventura, CA
Mehran - Ventura, CA
Very timely and fast. Thanks
Dispatched our HVAC technician to a health center in Ventura, CA. Site reported that the air conditioner for their product room with freezers and other perishable goods was not working, room too hot. Arrived onsite and inspected system on the roof. Unit had a failed contactor that our technician sourced locally a replaced. System is back online and working well.
Spring air filter change scheduled today at a grocery store in Ventura, California. Additional visit scheduled with management to return and complete the general inspection alongside control checks, coil cleaning for HVAC and refrigeration equipment and exhaust belt changes.
Completed winter air conditioning maintenance at a children's center in Ventura, California. Our technician swapped out the dirty air filters and checked all components. Unit #2 has a faulty fan motor that is overheating and should be replaced. Unit #1 has been reported as inoperable multiple times to the customer, and they are aware it needs to be replaced due to multiple component failures and overall condition.
4th Quarter AC preventative maintenance scheduled today at a commercial property in Ventura, California. Customer specific service, filter change only for site air handlers. All air filters swapped out, no deficiencies found and site comfortable. PM complete.
A shopping center in Ventura, California, reported that two sections of the building were not heating. Upon arrival, our technician found two commercial HVAC systems with issues. One EGCL system the thermostat programmed incorrectly, and the tech was able to resolve onsite. He also found a separate Lennox package AC with a deteriorated gas flex connector. The main gas meter was also turned off and locked out by the gas company. The customer will need to address the locked meter issue directly with the gas company, and we will quote replacement of the deteriorated flex connector in the mean time.
Our Ventura County technician returned to a commercial property to perform additional approved A/C repairs. Four units required new auxiliary condensation float switches to assist with recurring leak issues the site was experiencing. After installing all parts, drain lines were flushed and switches tested. Units draining and switches operating as expected. Job complete.
Dispatched our Ventura California technician to a hair salon to complete their Fall HVAC preventative maintenance. All components were inspected, air filters replaced. Unit is in poor condition and is missing ductwork connections in several places. These issues have been relayed previously to the tenant who is working with the landlord to resolve.
A customer requested a HVAC site survey for their new location in Ventura California. Our technician performed the survey, acquiring the single unit equipment data and noting issues. The Lennox unit is over 30 years old, operational but in poor condition. Will quote a replacement for the customer to consider. Survey complete.
Multiple air conditioning repairs were scheduled today at a commercial property in Ventura California. Three Carrier systems were repaired: #3 needed a new condenser fan motor, blade, capacitor and contactor. #4 needed its dual capacitor replaced. And unit #1 had two failed condenser fan motors, and had its blade, dual capacitor and economizer screen replaced. After completing all quoted work, the technician tested and cycled the units. Confirmed systems are operational again, job complete.
Our Ventura area commercial HVAC tech arrived at a furniture store to perform PM services. Replaced air filters, inspected electrical, motors, coils, adjusted belts and tested heating and cooling. Checked unit operations and noted that three Carrier units have deficiencies that we will quote to the customer. One unit, #1, has two defective fan motors and a failed capacitor that make it inoperable.
Our commercial refrigeration tech for the Ventura, CA, area arrived at a weight loss center to perform approved repairs. The Traulsen freezer had ice build up in the drain pan, found on the previous maintenance. Tech removed ice and adjusted drain pan slope so water can drain properly. During inspection found oil residue in condensate drain pan. Performed a leak check on the system and found small refrigerant leak on discharge line copper pipe, pipe was cracked. Technician recovered the freezer's refrigerant, repaired leak and replaced the filter drier. Pulled unit into vacuum and recharged with 404A refrigerant. Checked operations after making repairs, found no more issues. Monitored unit until temperatures dropped to freezing, job complete.
Winter maintenance performed by our commercial HVAC tech at a bank in Ventura, California. All belts were inspected, air conditioner filters replaced. Noted that the evaporator coil on the #1 Carrier unit was dirty and would need to be cleaned. Rest of units working normally, quoting deficiency to the customer.
Dispatched our Ventura County technician to a shopping mall with several locations suffering thermostat issues. Inspected both suites: first suite had incorrect programming that tech was able to resolve. Second suite had a failed thermostat that the technician sourced and replaced. Both stores cooling and comfortable again.
RESSAC a/c technician came out to clinic in Ventura to perform preventative maintenance on two York package units. Tech went on to the roof to replace filters and verify proper operation on the two units. Technician noted that both units were working perfectly.
A/C technician was sent to Firehouse Plaza to inspect 4 ton package unit manufactured by Bryant. Complaint was for no heat. HVAC tech found blown fuse. He replaced fuse and tighten all electrical connections. Unit is very old and would be a good candidate for new unit installation.
Jewelry Store in Pacific View Mall reported that cooling was not working. HVAC-R tech inspected 5 ton package unit manufactured by ICP and found loose control wiring. After cleaning up wiring terminations unit working again. Checked all amperage and voltages and found no other deficiencies to repair.
Repaired a Traulsen G31010JC freezer for a weightloss center chain.