Thousand Oaks, CA business & property owners in need of HVAC or refrigeration design, installation, maintenance, monitoring, repair or retrofits have called RESSAC first for the past 90 years. That’s because we are a third-generation, family owned company that prides itself in exceptional customer support, timely response and quality service. Don’t take our word for it, read our reviews below to learn more.
for Thousand Oaks, CA
Our Southern California refrigeration technician returned to complete approved work at a health center today. This freezer in Thousand Oaks required a new temperature controller. After installing the new part, our technician set temps to -5 and waited for the unit to drop to setpoint. System is online and operational.
Received a report regarding a freezer running at high temperatures in Thousand Oaks, California. Upon arrival, our technician found the system had dropped to 0 and was not correctly coming in and out of defrost. Determined that the defrost timer was failing. Sourced the part from the local supply house and replaced it. Cycled unit and brought it back below freezing. System is back online.
Scheduled refrigeration repairs for a commercial customer in Thousand Oaks, California, today. Their freezer needed a new fan motor that was supplied by the client. After removing the old motor and wiring in the new one, our technician restarted the system and confirmed unit dropped back to operating temperatures. Job complete.
Completed site walk/final inspection for full HVAC roof sweep.
Our SoCal installation crew returned to finish a full 15 unit roof sweep for a commercial customer, running new thermostat wire and connecting all drain lines.
A/C repair tech returned to a home goods store in Thousand Oaks, California, to complete approved repairs on the Trane package units. Two units needed new capacitors, RTU #1 needed a leak repair on the first stage, and unit #3 needed the condesner fan motor replaced. Our technician completed the repairs as quoted, confirmed that all units were up and running well again except for RTU #3. Will need to return with a guard for the condenser fan motor shaft, but store is cooling for now.
Belt replacements needed at a specialty imports supplier in Westlake Village, CA. Both the Carrier air conditioners had bad belts found on teh recent maintenance. Our technician swapped both belts, tested and confirm no other units in alarm with EMS.
RESSAC a/c technician arrived at a Thousand Oaks, CA, home goods store to investigate a water leak. Pinpointed the issue, condensate drain was plugged with debris. Cleaned and blew out line to resolve water leak. While onsite noted the #8 Trane air conditioner was making a loud humming noise. Found the blower motor failing, also will need to replace bearings and pulley. Will quote additional repairs to the customer.
Thousand Oaks a/c tech arrived at a vitamin store to investigate one of the units making a loud noise. Unit had been powered down to stop the noise and would no longer turn back on. Our technician discovered that the transformer had failed, was able to source and replace. Also found that the drive belt had torn, which had caused the original noise complaint. Unit working again after transformer and belt replacement.
A gift shop on Hillcrest Drive in Thousand Oaks, CA, reported a pipe leaking that may be HVAC related. Tech arrived and found their unit frozen up and the blower not running. After troubleshooting, pinpointed the issue to a fan relay not correctly wired to the board. Defrosted unit, fixed wiring, adjusted air handler for better pitch. Unit up and running again.
Specialty restaurant in Thousand Oaks, California, requested service for their kitchen hood. Our HVAC tech found the main hood exhaust had broken belts. Located belts at a nearby parts house, returned and replaced on both exhausts. Hood working well again.