In order to provide our exceptional commercial HVAC & refrigeration service to office parks, malls, retail stores and big box outlets in Santa Barbara, CA and throughout California, RESSAC employs great technicians, focuses on operational efficiency and keeps abreast of advancing technologies. Those are the key elements of every Santa Barbara, CA commercial assessment, design, installation, maintenance, monitoring or repair service we offer. Read our reviews below to learn what our business customers have to say.
for Santa Barbara, CA
Kevin was amazing. So knowledgeable and helpful.
Kristen Reilly - Santa Barbara, CA
Response from RESSAC Climate Control:
Thank you for reviewing Kevin's visit, Kristen. Our technicians greatly appreciate the feedback! We will have a proposal for preventative HVAC maintenance prepared for you with the equipment data Kevin obtained.
A commercial customer in Santa Barbara California was scheduled for air conditioning repairs today. Their #1 York system had a refrigerant leak on circuit #1. After performing the leak search and pressurizing the system, our technician found multiple leaks on both condenser coils, for both stages. The tech disconnected the circuits, leaving the system on fan-only operations, to protect the compressor. Will recommend coil replacement to customer, repair attempt not recommended.
Multiple HVAC repairs scheduled for our commercial customer in Santa Barbara, CA. One Carrier air conditioner required its condenser fan motor, blade and capacitor be replaced. A second unit had a pitted contactor and bad capacitor, and a third AC also had a pitted contactor. The technician completed all necessary repairs and tested the equipment afterwards, confirming all 3 units were functional again.
Our RESSAC technician arrived at a school in Santa Barbara, California, to survey all the commercial air conditioning equipment on site. Met with customer to discuss site needs, then inspected entire property. Gathered unit data for all air handlers, condensers and package units. Uploaded all asset information into service trade including air filter list. Visually inspected all units and found AHU #4 with a defective blower motor. Marked issue as a deficiency to quote. Survey is completed, will provide maintenance proposal for customer.
Can't get the smoke smell out of your commercial building after the recent fires Santa Barbara? We offer comprehensive preventative maintenance and cleaning of air conditioning systems. We can also inspect your duct-work and advise whether you need duct cleaning. Other fire remediation solutions include electronic air cleaners and carbon impregnated filters. Call us for a consultation.