In order to provide our exceptional commercial HVAC & refrigeration service to office parks, malls, retail stores and big box outlets in Riverside, CA and throughout California, RESSAC employs great technicians, focuses on operational efficiency and keeps abreast of advancing technologies. Those are the key elements of every Riverside, CA commercial assessment, design, installation, maintenance, monitoring or repair service we offer. Read our reviews below to learn what our business customers have to say.
for Riverside, CA
A health center in Riverside County requested service on their Traulsen freezer that was spiking high temperatures. Upon arrival, our technician found the unit low on refrigerant with a dirty condenser coil. Cleaned the coil, repaired the discharge service valve and recharged the system. Freezer back to -5 degrees and functional. Job complete.
Responded to a no-cooling request at a Riverside County commercial property. Our HVAC technician found no power going to the unit. Found the breaker in the electrical panel off, not tripped. Was told by the manager on duty that a sign technician had been out working on their light-up signage the day before. Labeled the breaker as RTU #1 to avoid issues like this in the future. Once powered on, system is working well with a 52 degree supply temperature.
A restaurant in Riverside California reported that the cooling drawer for the raw meet was not working properly. Our refrigerant technician arrived and inspected the unit. Found the cooling drawer operating as expected, no issues with the electrical or refrigeration parts. The drawers however are bent, wheels damaged and rails off-center. Will need to order new wheels and tracks for the drawers. Site will need to push hard on drawers in the meantime to make sure they shut correctly.
Responded to an urgent refrigeration call for a commercial customer in Riverside California. Our service tech found their Traulsen freezer running at 40 degrees and repeatedly tripping the breaker. Diagnosed the problem, found a potential relay burnt and a failed capacitor. A short circuit caused the electrical outlet to burnout as well. Sourced necessary parts from the local supplier, return and replaced the electrical outlet, relay and capacitor. Tested system and waited for it to return to correct freezing temperatures. Job complete.
A second technician arrived to help complete the multiple repairs at this site in Riverside CA. All units needed their evaporator and condenser coils chemically cleaned and the weather stripping on their filter doors replaced. The technicians completed the following: New economizer screens on RTU#2, replacing the crankcase heaters on units #3, #4 and #5, and compressor contactors on units #1, #2, #3 and #4. After completing all approved work, the technician checked out with EMS to confirm no units were in alarm and the site was comfortable. Job complete.
Dispatched our Riverside California commercial HVAC tech to a home goods store to complete approved repairs. Multiple Lennox air conditioners were scheduled for repairs. All units needed their evaporator and condenser coils chemically cleaned and the weather stripping on their filter doors replaced. The technician completed the following: New economizer screens on RTU#2, replacing the crankcase heaters on units #3, #4 and #5, and compressor contactors on units #1, #2, #3 and #4. After completing all approved work, the technician checked out with EMS to confirm no units were in alarm and the site was comfortable. Job complete.
Returned to a restaurant in Riverside, CA, to repair a 3 door freezer that had a refrigerant leak at the filter drier. After completing refrigerant repairs, tech also replaced the controller.Tested and cycled unit, repairs complete and freezer functional again.
Commercial controls technician for Riverside county was dispatched to complete work on new EMS installation . Finished software testing with TWave, corrected a software setup for RTU #4, confirmed wiring correct and VFD all functional. Energy management system installation complete, site communicating and running.
RESSAC is ready to serve you Riverside! We have NATE certified a/c technicians living in your area and servicing commercial buildings near you every day. We provide installation, repair, and maintenance services on all types and brands of HVAC and refrigeration equipment. All markets served including office buildings, distribution centers, warehouses, convenience stores, motels, restaurant and retail.