Long Beach, CA business & property owners in need of HVAC or refrigeration design, installation, maintenance, monitoring, repair or retrofits have called RESSAC first for the past 90 years. That’s because we are a third-generation, family owned company that prides itself in exceptional customer support, timely response and quality service. Don’t take our word for it, read our reviews below to learn more.
for Long Beach, CA
A cell phone store in Long Beach, CA, requested repairs on a vent over their manager's office. Vent was found dangling slightly and site was concerned it would fall. Technician was able to disconnect and reconnect with new straps to secure vent. Site also has dirty vents and filters. Will return with filters and clean vents per customer approval.
AC technician arrived at a beauty salon store in Long Beach, CA. Employees reported that their thermostat was blank and site was warm. After troubleshooting, the tech found the package Carrier unit down with three blown fuses. Parts were sourced, fuses were replaced and HVAC returned to proper operations. Space cool again.
Washed coils on a/c unit. Found no other issues.
A/c blowing warm air at a weightloss center in Long Beach, CA. Unit for the food room had a bad run capacitor for the condensing fan motor, and dirty coils causing the unit to shut off on high pressure. Replaced the cap and cleaned the coils. Unit is back up and running per par.