Lancaster, CA business & property owners in need of HVAC or refrigeration design, installation, maintenance, monitoring, repair or retrofits have called RESSAC first for the past 90 years. That’s because we are a third-generation, family owned company that prides itself in exceptional customer support, timely response and quality service. Don’t take our word for it, read our reviews below to learn more.
for Lancaster, CA
A shipping provider in Lancaster, California, had a failed heater in their ladies' restroom. Our local technician had diagnosed a bad motor, and returned today to remove the old part and wire in the new one. After replacing the grills he tested the system and confirmed heat was operational again. Job complete.
Summer AC filter change scheduled at a commercial property in Lancaster CA. New filters dated, basic inspections completed and air curtains cleaned. Belt issues found on units #7 and 2. Need to replace contactors on Carrier units #5 and #8. Will quote necessary repairs to customer, PM complete.
A cell phone provider in Lancaster California reported that their AC was down. Upon arrival our commercial HVAC tech found the thermostat had failed, and was not properly controlling the unit. Went to the local parts house and sourced a new thermostat. Installed and instructed staff on proper use of new thermostat. Also found a relay for the #2 ICP air conditioner chattering and sticking. Will quote to replace the relay, both units running at this time.
Cash advance shop in Lancaster, CA, reported a burning smell possibly from the HVAC. Tech inspected the Day & Night air conditioner and found it running normally, but did note blower motor running slightly warm. Will quote to replace motor, it is running for now. Changed filters while onsite, filters were clogged. Replaced filters and check units operations . Found no smell at time . Found motor running hot for unit 2 . Recommend to change as it is the original motor .
Received an ER request from a mobile provider in Lancaster, CA. Their #2 ICP air conditioner was down upon arrival. Upon inspection found unit with a chattering cubical relay that will need to be replaced. Went to local parts house to source but was not available. Will order parts to ship.