Anaheim’s Commercial Refrigeration & AC Experts
Anaheim, CA business & property owners in need of HVAC, control system or refrigeration repair, design, installation, maintenance, monitoring, or retrofits have called RESSAC first for the past 90 years. That’s because we are a third-generation, family owned company that prides itself in exceptional customer support, timely response and quality service. Don’t take our word for it, read our reviews below to learn more.
for Anaheim, CA
Comprehensive and professional.
Kim - Anaheim, CA
Javier did a great job with the assessment and photos. We have a clear idea of how to proceed with repairs to eliminate the problem.
A freezer manufacturer dispatched a request to replace a failed power cord for one of their customer's freezers. New cord was shipped to the site and our technician removed the existing cord and replaced with the new one. Tested for proper operations after repair, freezer back to freezing temperatures again.
Approved cooler repairs scheduled at a restaurant in Anaheim California. The customer's expo table needed to have the defrost timer replaced and rewired, and a new digital electronic thermostat installed. After making all approved repairs, our HVACR technician tested operations and confirmed the unit was operational again.
Dispatched our Anaheim CA refrigeration service tech to a restaurant, who reported their stand-up cooler doors needed repair. After inspecting the cooler, the tech determined that the doors could not be repaired. Steady use has exposed the insulation and there is no option for this door type to repair. Quoting two new doors for the site.
A restaurant in Anaheim California requested service. Their expo table had two fans that were frozen over solid with ice. Our technician troubleshooted the system, finding the suction pressure dropping. Noted that the line-set is incorrectly sized at the discharge line, and the defrost clock was set for 6 hours at night without any during the day, and that it was wired incorrectly to not shut down the compressor. Will need to source necessary parts and quote to repair.
Summer HVAC PM scheduled at a management office in Anaheim Hills CA. Site has one split system, which needed filters changed and both the air handler and condenser sections inspected. No issues found at this time, split system is working well and site comfortable.
Dispatched a repair technician to investigate a minisplit that had gone down. Found unit in poor condition, multiple leaks in the condenser coil. Do not recommend repairs as unsure they will hold. Will quote non-warrantied repair and a replacement option to customer.
RESSAC tech dispatched to Anaheim, California, to inspect a swamp cooler that was leaking onto the roof. The technician surveyed the unit, found it leaking due to damaged drain line that would need to be rerun. Shut off the equipment per management's request to stop the water damage. Reported back with photos and details to quote repairs to the customer.
A/C technician dispatched to multiple maintenance jobs in Anaheim.
Performed quarterly maintenance on air conditioners and refrigeration